Top Rated Local Heating & Air Conditioning Repairs Services
See what your South Austin neighbors are saying about our HVAC services below.
for Austin, TX
Our Reviews by City
Anne - Austin, TX
I appreciate being grandfathered into service plan. It means a lot to me.
Thanks for excellent work
Sharon - Austin, TX
Zelda - Austin, TX
Zelda - Austin, TX
I am very satisfied, Ray explained the maintenance and repair that was done.
Ursula - Austin, TX
C - Austin, TX
Hayley - Austin, TX
Ryan and the crew were very professional and hardworking. Can’t thank Ryan enough for all his help.
Great job, Don!
Dee - Austin, TX
Don was able to find my problem and fix it to my satisfaction! And explain to me what had happened .
Keith - Austin, TX
We use Garner Heating and A/C multiple times a year. Always professional service at a reasonable price. Wouldn't use anyone else.
Always great service!
John - Austin, TX
I have received heating and air-conditioning services for nine years from Garner. Service has always been top notch! When my AC failed on a very hot Saturday morning, Garner set up two window units at no cost to keep me cool thru the weekend, then replaced the motor first thing Monday morning.
Serviced a spit system Carrier system.
Installing two home comfort systems on Fox Run Drive. Two new high efficiency furnaces and two new complete AC systems.
Installed 3.5 ton carrier heat pump closet system
Cooling system check. Spring preventative maintenance on a Carrier split AC system.
Maintenance Agreement renewal for 1 system for 2 years. 🙂
Replacing a badd condensate pump on an old R22 freon system.
Performed in AC inspection to ensure low energy bills and maximum cooling efficiency.
Performing equality AC inspection to ensure low energy bills.
Complete voltage enhancement system renovation. Cooling system check up. Spring preventative maintenance on an American Standard split AC system
Performing two AC tune ups on Redmond Rd. Helping our customers save money during the hot summer months by making sure that their system is clean and all parts are working properly.
Installed new thermostat wire, replaced, contactor, washed both outdoor coils, found loose gas line and tightened connection and tested.
Traced low voltage short to outdoor condenser.
Performed annual cooling inspection. Cleaned coils, changed filter, checked amp draws on compressor and condenser fan motor, checked capacitor, checked contactor, sprayed for ants and changed filter.
Replaced contactor, capacitor and installed and compressor saver start kit
Spring cleaning. Preventative maintenance cool check.
Cool check preventative maintenance.
Cooling check preventative maintenance on 2 carrier and 2 trane split systems.
Cooling inspection on a Heatpump system. Checked the charge, amp draws on all loads, checked capacitors and contactor, checked blower motor shaft and cleanliness and performed an electronic leak test on evaporator coil.
Fixing a low voltage short on a Carrier Heat pump.