Top Rated Local Heating & Air Conditioning Repairs Services
See what your South Austin neighbors are saying about our HVAC services below.
for Austin, TX
Our Reviews by City
Always timely with initial inspection after a call and can repair onsite in lots of cases
Lisa - Austin, TX
Can't be more pleased with response time, quality of diagnosis, repair and pricing. So reliable and trustworthy
Deborah - Austin, TX
Garner AC was quick to get someone to my house. The tech was friendly and courteous!
Just good old fashioned service
Alberto - Austin, TX
Family owned business that cares about their customers
Quick to respond and easy to communicate with. Answered all my questions
Lucinda - Austin, TX
David - Austin, TX
Ursula - Austin, TX
Naturally we all like for our big ticket items, like an air conditioner, to last for more then 10 years without any problems. However, in today's time that is sheer impossible. But I got good service and appreciate the mechanic's knowledge and professionalism. I feel he did an excellent job, I am very satisfied.
Anne - Austin, TX
I appreciate being grandfathered into service plan. It means a lot to me.
Thanks for excellent work
Sharon - Austin, TX
Zelda - Austin, TX
Zelda - Austin, TX
AC repair in menchaca with duct cleaning and tune up
AC repair manchaca Texas
Air conditioning maintenance with duct inspection cleaning and efficiency upgrades
Replacing an air conditioning and heating system in manchaca
AC repair in San Leanna
Performed 1 system heater tuneup on a gas furnace, checked inducer motor, checked negative pressure switch, cleaned barometric tubing, checked hot surface igniter, cleaned flame sensor, checked gas valve and pressures and checked blower motor and shaft
Replaced a bad igniter inside the American Standard gas furnace system.
Heater tuneup on a gas furnace. Checked inducer motor, checked negative pressure switch, cleaned barometric tubing, checked Hot surface Igniter and ohmed, cleaned flame sensor, checked heat rise and checked blower motor bearings and shaft
Heater tuneup on a gas furnace. Checked inducer motor, checked negative pressure switch, cleaned barometric tubing, checked hot surface Ignitor and ohmed, cleaned flame sensor, checked heat rise and checked blower motor bearings and shaft.
Replaced a bad voltage absorber inside the Carrier condenser. Perform system inspection and everything is in good working order at this time.
Cleared and treated a clogged condensation drain on a split AC unit
Cool system check. Spring and summer maintenance tune up on a Carrier split AC heat pump system.
Performed QC on new high efficiency Carrier system. Performed an air balance of the home and adjusted fan speed for optimum dehumidification capability.