Top Rated Local Heating & Air Conditioning Repairs Services
See what your South Austin neighbors are saying about our HVAC services below.
It costs around $200-$400 to replace an AC line in Austin, TX. The cost of the replacement can vary depending on:
- The cost of the AC line.
- If other parts also need to be replaced.
- The contractor’s hourly rate.
A few reasons you may want to replace your home air conditioner rather than repair it in Austin, TX include:
- Your air conditioner is over 10 years old.
- Your air conditioner breaks down often.
- Your air conditioner does not cool you home effectively.
Another reason you may want to replace your home air conditioner rather than repair it is if the cost to repair it is more than half of the cost to replace it. A newer and more efficient unit will be able to run smoother and cost you less on energy each month. To get your home air conditioner replaced, call us today.
If your home air conditioner has a higher SEER rating, it can cool your home more efficiently than other systems. Since the higher SEER rating can make your air conditioner more efficient, it will also typically cost you less on energy costs each month. Although, you should ensure that your air conditioner’s SEER rating matches your specific needs to ensure that it is able to work its most efficiently in your area’s climate. To learn more about what SEER rating your air conditioner should have, give us a call today.
for Austin, TX
Our Reviews by City
Zack - Austin, TX
They did a great job, were on time, and very thorough when checking everything out.
Mr. George Torres
Lopez - Austin, TX
Mr. George Torres was a very professional person He was polite and very good at answering questions. He was punctual for the appointment. He did a very good job.
Rodriguez - Austin, TX
Booker - Austin, TX
K. Cox - Austin, TX
I had them service my elderly Mother's home heating system. Very good service and informative of any issues.
Grayson - Austin, TX
I would appreciate it if your service packages could be divided into two yearly payments instead of one large payment.
Place services, next day they we’re servicing my air conditioning. Fast and reliable service
Rodriguez - Austin, TX
The owner personally called me same day of service and tried to check basic step before sending someone.
Urgent A/c issue
Garrett - Austin, TX
Very happy with the great, prompt service I received.
Anne - Austin, TX
Very thorough. Explained everything. We are very pleased.
Air Duct cleaning
Frank - Austin, TX
Ethan and Jason did a great job cleaning our air ducts. They were polite and professional! I highly recommend Garner!
Found a drain line that was clogged and tripping the float switch. This happened because the filter in the system is too small allowing bypass where dirt is getting onto the coil and then to the drain causing the backup. I cleared the drain and treated with Viper pan and drain treatment. I also spoke to them about our Maintenance plan. They agreed and I performed the check on the system I was working on which was the Payne system. System checks out great.
Whole home generator and service upgrade
Performed diagnostic on the Reme Halo and found that the bulb had failed. Replaced Reme Halo and discounted service per part credit. System working upon completion of replacement.
Performed diagnostics on a Carrier heat pump system. Found the 45-amp breaker tripped and 35/5 voltage enhancement system under tolerance. Installed a new 40-amp breaker and voltage enhancement system. Components verified and secured. System is operational at completion of
Performed diagnostics and found an issue with the electrical wiring on the Carrier heat pump system at the air handler. I also found that the outdoor voltage enhancement system was under tolerance and customer has chosen to move forward with basic repairs. System is operational in heat mode after completion of repairs.
Performed heating tune-up on American Standard heat pump. Please see attached checklist for full tune-up details.
Gave 2 options for replacing a 2.5 ton heat pump system
Performed heating tune-up on a Carrier heat pump system in closet. Found voltage enhancement system under tolerance and repairs completed. System up and heating
Performed heating tune-up on an American standard gas system. Filter changed and dated, and filter rack vacuumed and cleaned. Drain treatment performed and sequence of operation completed without issue. Electrical components checked and gas pressures verified. Damage at flame sensor was brought to Mr. Williams attention and he chose to have it replaced. New sensor has been installed, secured, and tested. System is up and heating.
Performed diagnostics and found expansion valve at outdoor unit damaged and restricting refrigerant flow. Chris will reach out to us tomorrow if he wants to go forward with repairs; he is going to speak with ARS first since they installed the system. I did replace the voltage enhancement unit per customer's request.
Performed heating tune-up on Carrier gas system upflow in closet. Filter (16x25x1) changed and dated and drain treatment performed. High and low voltage wiring secured. Outdoor condensing unit’s electrical components verified in spec and condenser washed off. System is up and heating.
Performed heating tune-up on a Lennox gas furnace. Sequence of operation completed without issues. Drain treatment performed and all wiring/electrical components and gas input verified. Outdoor condenser unit washed off and electrical components in spec. System is up and heating. Duct and plenums in poor condition; see attached estimate for repairs.
Installed five Reme Halos in the air handlers serving the church sanctuary and upstairs offices. Once Keith connects the high voltage to the transformers, we will install the 6th one upstairs.
Routine heating maintenance performed on a Carrier 3.5-ton heat pump up-flow system in closet. Drain maintenance was performed and line is clear. All interior electrical components were tested, and wiring secured. Filters have been recently changed out by customer and the return side condition of evaporator coils have been noted in good condition. Voltage enhancement system and refrigerant on target and unit washed off. System is up and heating.
Routine heating maintenance performed on Carrier gas up-flow system. Sequence of operation completed without any issues. All safety features tested, drain treatment performed and existing filter in new condition. Fuel output to furnace in spec and flame sensor has been cleaned off. Outdoor unit’s voltage enhancement system verified, and unit washed off. System up and heating.
Routine heating maintenance performed on a Bryant gas system. Sequence of operation completed without issue and all safety features tested. Wiring secured, drain treatment performed and filter in new condition. Outdoor unit’s voltage enhancement system has been replaced and condenser washed off. Also fuses at disconnect tested and working order. System up and heating.
Routine heating maintenance performed on a Carrier gas system. Sequence of operation completed without issue and all safety features tested. Drain treatment performed and filter changed and dated. Outdoor unit’s voltage enhancement system verified in spec and coil washed off. System up and heating. Customer also renewed maintenance agreement for another year.
Routine heating maintenance performed on a Carrier up flow gas system. Sequence of operation completed without issues. All safety features tested, flames sensor has been cleaned off, outlet gas pressures in spec, and drain treatment performed. Wiring at gas furnace and outdoor unit secured. Filters in new condition. Outdoor voltage enhancement system verified, and unit washed off. System up and heating. Customer has renewed their maintenance program for another year.
Routine heating maintenance performed on an American Standard gas system. Sequence of operation completed without issues and all safety features tested and secured. Amps at air movement system in spec, flame sensor cleaned off, three burners in new condition and drain treatment performed. Outdoor unit has been washed off and voltage enhancement system verified in spec. System up and heating.