Air Conditioning Repair Services in Mountain City, TX
Whether it’s an emergency AC repair, having to replace your old heating and air system, or installing a new unit or seasonal preventative maintenance, we can offer you and your family the peace of mind at a cost that won’t break your budget in Mountain City, TX.
Your home air conditioner may be running but not cooling in Mountain City, TX because:
- Your thermostat is set to ON rather than AUTO.
- Your air filters are dirty or clogged.
- Your air conditioner’s drain line is clogged.
- Your air conditioner has a refrigerant leak.
If you are encountering one of the first two issues, then it can be an easy fix. If you are encountering one of the last two issues, you will need someone with HVAC knowledge to repair your air conditioner. Give us a call today to have your air conditioner repaired.
The average cost to repair an air conditioner in Mountain City, TX is around $300-$600. However, some things can cause the price to fluctuate, such as:
- The level of the repair.
- The price for any replacement parts.
- The contractor’s hourly fee.
Some repairs can be quite costly, depending on how extensive they are and if they cause further damage to the function of your air conditioner. Maintenance plans are a great way to prevent unexpected and costly repairs since you can spot problems before they become large repairs. To get your air conditioner repaired, contact us today.
It costs about $5,000-$8,000 to install a new furnace and air conditioner in Mountain City, TX. However, some things that can cause the cost to vary are:
- The size of your house.
- The type of HVAC unit you want.
- The contractor’s hourly rate.
Having a new furnace and air conditioner can save you money on your monthly energy bills, as well as increase the overall value of your home. To find out more about getting a new HVAC system installed in your home, call Garner Heating & Air Conditioning today.
When your air conditioner isn’t cooling your home in Mountain City, TX, you should check:
- If your thermostat is set correctly.
- If your air filters are dirty.
- If your air conditioner has a leak.
If your thermostat is already set to cool, check to make sure it is also set to AUTO rather than ON. Additionally, if you find that your air filters are dirty, replace them with new air filters. If your home air conditioner is still not cooling your home, you should call an HVAC technician to repair it. To get your home air conditioner repaired, contact us today.
It costs around $300-$550 to fix and repair your home air conditioner in Mountain City, TX. However, the cost can fluctuate depending on how extensive the repair is, whether replacement parts are required and the contractor’s hourly rate. For instance, having a condenser fan motor replaced can cost up to $700. To learn more about getting your home air conditioner repaired, call Garner Heating & Air Conditioning today.
Yes, air conditioning coils can be repaired if the damage is not too severe. That being said, even though you can repair an evaporator coil, it is typically better to have it replaced rather than repaired. The material that makes up the air conditioning coil can wear out over time through use and the cost to repair it can sometimes outweigh the cost to replace it. If you are thinking about getting your air conditioning coil repaired or replaced, give us a call today.
See what your Mountain City neighbors are saying about our services below.
for Mountain City, TX
Our Reviews by City
Cass - Mountain City, TX
We love Garner A/C and their crew. Very competent, friendly and informed us of each thing he was doing to fix our problem. Thank you!
McClendon - Mountain City, TX
Great job. George was most efficient and explained what he was doing in terms that anyone could understand.
As usual, great service.
Limmer - Mountain City, TX
Garner never disappoints. Always can count on great service by a local business.
Semi annual service
Cass - Mountain City, TX
Lee - Mountain City, TX
As always, 100% satisfaction with the service, workmanship, products and people of Garner.
Chris - Mountain City, TX
Clyde - Mountain City, TX
Laverne - Mountain City, TX
On time, cautious, thorough
Ed - Mountain City, TX
Fast response time. Knowledgeable service staff.
Jennifer - Mountain City, TX
In November 2018 my Carrier Heat Pump of 24 yrs crashed. Garner gave me several Carrier options to consider and within 2 days had a courteous, knowledgeable crew at my home installing the unit. I opted for ductwork replacement also and was amazed at the teamwork and how clean the crew left my home. The unit is quiet and variable speed for greatest economy. Love the new digital thermostat.
Performed further diagnostic on an American Standard air conditioner and found low-voltage short at control wiring for outdoor system. Presented customer with options and have chosen to move forward with replacement of control wiring to condenser and adding electrical conduit to protect it from the elements. Repairs and performance testing completed, and system is now operational.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. Partial clog found in condensate drain line. Drain line was cleared and treated. No other major issue were found. Condenser coil cleaned. Electrical disconnect confirmed in and on. System set to 71° per customer. System was running at time of departure.
Performed diagnostic on an American Standard heat pump system and found supply buckets not sealed letting rock wool insulation into home. Also found a primary drain clog interfering with cooling cycle. All supply buckets have been sealed with mastic in attic where buckets and drywall meet. Primary drain was treated and cleared. Dirt and leaves have been vacuumed out of the condenser and the coils have been cleaned. Electrical and refrigerant charge verified, and system is now operational.
Air conditioning plumbing termination point is routed to utility washer box. Primary drain has been cleared and primed. System back up.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. Condensate drain line was found to have a clog. Drain line clog was cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System set to 77° per customer. System was running at time of departure.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system with no issues found. Drain line cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System set to 74° per customer.
Performed cool check. Drain line was cleared and treated. Checked electrical, safety, mechanical, and performance of the system with no other issues found. Electrical disconnect confirmed in and on. System set to 74° per customer.
Performed cool check on AC system. Drain lines cleared and treated. System performance was in spec. Please see attached checklist for full tune-up details.
Performed cooling tune-up on an American Standard gas system. Please see attached checklist for full tune-up details.
Performed heating tune-up on a heat pump system. System is operational.
Performed heating tune-up on American Standard heat pump up flow in hallway. Drain treatment performed and filters changed out recently. Safety features tested and the interior air handler cabinet in clean condition. Outdoor condenser unit washed off and electrical and refrigerant charge in range. System is up and heating.
In the notes on the last visit George indicated that there may be a leak in the evaporator coil, and we need to check it again on our next visit. Refrigerant pressures are where they are supposed to be at this time, and I put my leak detector on the evaporator coil and did not get any hits. Everything is working and we will check again on the next visit.
Preformed heater tune-up on a Carrier heat pump system in attic. Checked electric heat strips and treated condensate drain. Also checked heat rise and motor bearings. Cleaned outdoor condenser coil and checked value on voltage enhancement system. Sprayed JS-685 ant spray around panel opening. System working well at this time.
Performed heating tune-up on a Carrier heat pump up-flow system in hallway. Reme Halo bulb has failed and needs replacement. Emergency heat has been tested and in working order. Drain treatment performed and 20x20x1 filter changed and dated. Refrigerant charge verified and outdoor unit washed off. System is up and heating. Customer has renewed maintenance agreement for another year.
Routine heating maintenance performed on a Carrier gas system. Sequence of operation completed without issue. Safety features have been tested, voltage enhancement system verified, and gas output reading 9.8 in spec. Drain treatment performed and customer has recently changed out 20x25x4 filter. Did find a fault at the thermostat. New thermostat has been installed and tested in all modes. System heating and cooling properly.
When I arrived, I found the system to be very low on refrigerant. I found the leak in the evaporator coil and gave the customer their options. They chose to have it replaced at the silver level on Friday, 10/23/20. Repair will be charged to the customer’s Greensky account.
Adjusted the louver on the mini split head so it would close completely.
Routine heater maintenance on an American standard. Sequence of operation completed without an issue. Drain treatment performed and filters in good condition. All safety features and gas components tested and verified. Outdoor unit refrigerant charge has been recorded per customers feedback of a possible leak, but none found, and condenser washed off. System up and heating.
When I arrived, the customer informed me that the mini split system did not seem like it was blowing the way it normally does and that they thought it had frost on it. When I turned it on and checked the temperature split from return to supply, I had a 22-degree difference. 70.4-48.0. The coil is clean, the filter was cleaned yesterday, and the blower wheel is moving plenty of air across it. Everything is working at this time and I am not sure why it was having issues yesterday. The customer will call if the issues present themselves again.