Your Trusted AC Repair Company
Garner Heating and Air is a top-rated local heating and air conditioning contractor that has served residents of Driftwood, TX since 1998. You have enough to worry about already, don’t panic when your AC system isn’t working correctly. Call the experts at Garner Heating and Air the local company you can rely on in Driftwood, TX.
Your air conditioner capacitor is the device that provides your unit with the initial power boost it needs to cycle on. It also supplies power to the AC that allows the unit to complete a cooling cycle. Some signs that your capacitor may not be working include:
- The air conditioner will either not turn on or take a while to start after you turn it on.
- The unit is not blowing cold air.
- There is a humming noise coming from the AC.
- The unit keeps shutting down.
On average, you can expect your AC unit to last between 10 – 15 years. To prolong the life of your unit, make sure to:
- Have it serviced regularly – Maintenance service has been shown to not only help central air conditioning systems last longer, but also run more efficiently and ward off future breakdowns.
- Run it reasonably – Our Texas summers can be brutal. However, if the temperature hits over a hundred degrees outside, trying to cool your home to 60 degrees will put undue stress on the unit and shorten its working life.
- Change filters on time – Changing the air filters in your home helps your AC run more smoothly by allowing air to circulate easier. New air filters also collect more dust and dirt that will prevent extra debris from getting into the system.
To learn more, contact the experts at Garner Heating & Air Conditioning today! We offer professional AC installation services guaranteed to keep you and your family cool for years to come.
On average, the repair cost to replace an AC capacitor runs around $200 – $300 for a professional technician to complete. You can expect the job to take between 1 – 2 hours.
For a more accurate estimate, Garner Heating & Air Conditioning can help! We offer “Peace Of Mind” pricing, which means we provide the price before doing the repair and never add an additional charge on top of it. Contact us today to learn more!
Our services include:
Giving you a price before we start service
Guarantee on repairs for a year
We’ll never tack on charges that you don’t need
All of our technicians are N.A.T.E. certified, clean cut professionals that you can trust!
Whether it’s an emergency AC repair, having to replace your old heating and air system, or installing a new unit or seasonal preventative maintenance, we can offer you and your family the peace of mind at a cost that won’t break your budget.
See what your Driftwood neighbors are saying about our services below.
for Driftwood, TX
Our Reviews by City
Leblanc, Heather - Driftwood, TX
Everything was wonderful!!!
Friendly, knowledgeable and gave good advice
James - Driftwood, TX
Awesome service, Quick turn around.
RB - Driftwood, TX
A/C went out and Garner was able to dispatch on short notice. Ray was very professional and thorough. He quickly identified our issue and got us back up running in no time.
Ellie - Driftwood, TX
Garner’s there when you need them, which really counts when you have heating or AC problems.
Neal - Driftwood, TX
Max came to our house on a Saturday and quickly diagnosed the the problem. Options and prices were given to do a temporary repair verses replacement of the entire system. The installation team arrived promptly as scheduled. Technicians paid attention to every detail of the job and thoroughly cleaned their work areas when finished. After final testing, Ryan went over each process that they had performed and gave an explanation of the warranty, system operation and maintenance requirements. Overall experience was excellent and I highly recommend Garner Heating & Air Conditioning.
John - Driftwood, TX
The tech changed a start capacitor. Should have been a nominal $150-$200 repair. Took him 5 minutes tops as I had removed access panel already. Before he started the 5 minute changeout, he presented me with 5 options ranging as high as nearly $700 for “extras” like repairing burned wires (seriously? an extra?) and etc. Top (his recommended) price was nearly $700. My experience was overall good but only because I’m an educated buyer. I did not appreciate the blatant upsell attempt. You all have been better than that before now.
Performed diagnostic and found primary failure at air movement system and found outdoor voltage enhancement system to be weak. Options were presented to customer and have chosen to move forward with silver level air movement system renovation. New air movement and voltage enhancement systems have been installed. Performance testing also completed. System is operational.
Performed cooling tune-ups on a 2-ton and a 5-ton heat pump system. The customer let me know that they were having intermittent issues during cooling cycle. I found that both voltage enhancement systems were failing and found the 2-ton system low on refrigerant. Options presented for repairs and customer has chosen to move forward with new voltage enhancement systems on both units and the voltage performance system on the 5-ton. I also added 6 pounds of refrigerant to the 2-ton unit. Sealant was discussed with customer as an option but have decided not to have the sealant product added. Both systems are now back on target and are operational.
Estimate for new heat transfer media coil and replacement of large condensation drain pan entered. If customer moves forward with both repairs at the same time we will provide $250 discount to the total of both repairs.
Performed Deluxe tune-up on one of the two systems (5-ton first floor). Found the air handler drain pan to be dirty and outdoor voltage enhancement system under tolerance. Presented options for cleaning and customer has chosen to move forward with recommended cleaning. Completed cleaning of air handler and replaced voltage enhancement system. Checked system after repairs and everything is operational at this time.
When I arrived, I found the primary drain line to be backed up and causing the safety overflow switch to trip. I presented the customer with her options and she chose to have it repaired at the bronze level at this time. After performing the bronze level repair everything is draining and working properly at this time. I also spoke with the customer about having a 4-inch media air cleaner installed so she does not have to get up on ladders to change her 1-inch filter every month. She declined at this time but said she would think it over and reach back out when ready.
Installed 24x25 Carrier, 4 inch media cabinet and filter. Completed QC.
Please see attached quotes for your HVAC replacement
Performed heating tune-up on a 4-ton heat pump system. Found safety switch damaged and I have completed the repairs.
When I arrived and performed the diagnostic, I found that the ignition and combustion system had completely failed and was not bringing the furnace on. I presented the customer with her options and she chose to go ahead and have it replaced at the silver level. After performing the silver level repair everything is coming on and working at this time.
Performed platinum level electrical repair on heat pump system in attic (on roof). Fixed electrical wiring connections and washed-out evaporator coil. Sprayed Viper cleaner in drain pan and cleaned cabinet. Performed voltage enhancement system replacement and cleaned out electrical cabinet. Sprayed JS-685 ant deterrent around openings and washed outside condenser. Preformed safety testing and checked system operation in each mode. System working at this time.
After performing the diagnostic, I found the furnace control board to have completely failed by not sending the signal through to turn on the furnace. I presented the customer with her options and she chose to have it replaced at the basic level at this time. I ordered the part, and we will be coming back out tomorrow to install the furnace control board.
Installed line set with insulated PVC drain and control wiring. Equipment ready to be installed once ground is smoothed and sheetrock finished.
Found Carrier heat pump system offline due to drain issue. Drain treatment performed and system back up and cooling. All other values recorded. There was no charge for this visit, but if further issues persist, the customer knows we will need to discuss a more permanent repair.
Performed maintenance on an American Standard 3.5-ton heat pump. Drain treatment performed and 20x30x1 filter changed/dated. Outdoor unit has been washed off. Refrigerant charge and electrical components verified in spec. System up and cooling. Customer has renewed their maintenance for another year.
Found that the system is cooling properly at this time. Based on the two visits I’ve made this summer, it may be time to consider supplemental air conditioning for these days over 100 degrees. The system is designed for max temps 98-99 degrees outside. A system should not be designed for 105+ because most of the year it will be over-sized and cause other problems. No charge for today's visit.
Found voltage enhancement system had failed on a system that I worked on a year ago. We never gave them a safety inspection. And the part is covered under our warranty. System is working now that I changed the voltage enhancement system.
Don’t take our word for it–see what your neighbors are saying about our AC and heating services in our testimonials.
We are very proud to serve the Driftwood community with professional, honest and reliable certified experts that are dedicated to you and your family with the highest level of customer service. We are continually training our staff to handle any AC repair problem with the fastest service possible.
When your air conditioner isn’t working or you notice higher energy bills, it’s time to call the experts at Garner Heating and Air. Get the peace of mind that you deserve knowing your repair or installation was done correctly. We’re just a phone call away at 512-392-2000.