Heating & Air Conditioning Repair Services in Kyle, TX
They say home is where the heart is, and there’s no doubt that’s how we feel about Kyle. It’s the very place the Garners have chosen to hang their hats! It’s safe to say that you want your heart, and your home, to be as comfortable as possible and in Central Texas, this means that your heating and cooling situation better be top notch. With three decades of replacing, maintaining and repairing heaters and air conditioners, and all the experience that comes with it, the HVAC professionals at Garner Heating & Air Conditioning are pleased to offer our heating and air conditioning services to all our neighbors in Kyle.
Your heating and cooling system is one of the pricier items in your home – you want to make sure that the people you entrust to work on the system are knowledgeable and professional. Our AC and heating specialists are N.A.T.E. certified and have years of experience optimizing existing systems and expertly designing new systems. Heat and AC repairs in Kyle, whether it’s for your system’s heat pump, gas furnace, or any of your cooling elements, has never been easier.
The most effective way to keep your indoor air clean is to invest in an air purification system. There are different ones from which you can choose. Depending on the pollutants present in your home, a certain one will work best for you. Garner Heating & Air Conditioning can help determine what is going on with your indoor air and how best to keep it clean. We offer a number of different high quality IAQ products guaranteed to improve the indoor air quality in your home. Contact us today to learn more!
If your air conditioner freezes, follow these steps to get your unit functioning again:
- Turn off the unit from the breaker. This will allow the unit to thaw. FYI, thawing could take an entire day.
- Do not remove the ice by hand to avoid damaging the unit.
- After thawing, dry the coils by turning back on your unit but on the fan setting only. This helps circulate air and dry the coils quickly.
- Turn the AC back on to see if it operates without freezing over.
On average, Kyle TX residents can anticipate paying around $350 for minor air conditioner repairs, or a range of $165 – $550. Larger repairs can cost quite a bit more, even upwards of $2,000 depending on what is wrong.
For a more accurate price, contact the team at Garner Heating & Air Conditioning. Our technicians will provide accurate and affordable repair services, guaranteed.
See what your Kyle neighbors are saying about our services below.
AC Replacement Kyle, TX
When a replacement is needed, our certified technicians take pride in designing from scratch a plan to make sure that your infrastructure meets the needs of your new equipment. Often, the airflow and design of preexisting equipment would poorly support a new system. Our Kyle AC and heater experts will go in and maximize the efficiency of your new system, keeping your system performing optimally for many years to come.
Whether your needs are commercial or residential, our Kyle AC and Heating specialists will ensure your Central Texas space is as comfortable as you need it to be. Contact us today.
for Kyle, TX
Our Reviews by City
Liz - Kyle, TX
Livermore - Kyle, TX
I’ve been using Garner for a number of years…always on time, always efficient and explains all details of services provided. System continues to work well which is the real proof that the work they perform works.
Niedzielski - Kyle, TX
Very helpful in explaining and correcting our temperature issue.
Clear and direct information
Zuckman - Kyle, TX
I found the service technician was very clear when explaining the problem and the suggested solution.
Aimes - Kyle, TX
My tech did a great job checking everything and making sure it’s in good running order .
Friendly, listens to me, seems to care what service quality he provides
Patsy - Kyle, TX
Professional, timely estimate
Jim - Kyle, TX
Excellent service, a tad pricey
Saunders - Kyle, TX
George Torres did a wonderful job checking our two units and making needed adjustments. Since his visit, the units seem to be responding better and more quietly. Like so many other service costs, this visit cost more than in the past. Because of George's A-plus work, we don't mind the cost so much.
Morrison - Kyle, TX
Very professional! On time, knowledgeable, and was very helpful with the explanation of the problem
Harper - Kyle, TX
Its always a pleasure to see the Garner team come to the house. I know they keep my system in top shape.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system with no issues found. Drain line cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System set to 75° per customer.
Performed the AC tune up and everything is working at this time. I did notice the filter was dirty and let the customer know it should be changed ASAP.
After performing the diagnostic, I found that the primary drain line was backed up and dripping water on the platform. I presented the customer with his options, and he chose to have it cleared at the basic level. After performing the basic level repair everything is draining properly at this time. I did offer maintenance to the customer, but they declined at this time.
Performed diagnostic and found outdoor voltage distribution system failure. Presented options and customer has chosen to move forward with a new voltage distribution system. Repairs completed and tested. Also installed new 3-amp fuse at air handler. System is now operational.
After performing the diagnostic, I found that the voltage enhancement system had completely failed. I presented the customer with his options, and he chose to have it repaired at the basic level. After performing the basic level repair everything is coming on and working at this time.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system with no issues found. Drain line was cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System was returned the temperature by customer.
Performed cooling tune-up on a Carrier gas system.
Supply plenum has been reattached to equipment and sealed all the way around with mastic. This system is still operational. On the other unit, return duct has been remade, secured, and sealed. Both systems are operational.
Performed inspection on a Carrier heat pump system. Please see inspection checklist for details. I did find that the interior air handler cabinet was in poor condition. Discussed options with customer and they have chosen to move forward with gold level rejuvenation cleaning. Air movement system was removed and cleaned, and heat transfer media coil was cleaned in place. Safety feature was added to avoid any future issues with water damage. System is fully operational.
nstalled new cased coil and condensing coil. Reused furnace and return air plenum. Installed new zoning system with dampers and zone board. Rebuilt primary and secondary drains with SS-2 and SS-3 safety switches. Installed line filter dryer and pressure tested system for extensive leak check. Pulled deep vacuum and charged system to factory specs. System benchmarked and operating at this time.
Perform diagnostics and found outdoor air movement system with internal hardware damage. Also, found outdoor voltage enhancement system failure. Presented repair options to the customer and they have chosen to move forward with new air movement system and new voltage enhancement system. Components have been installed, secured, and tested. Refrigerant charge on target and condenser washed off. There is a 16x30x1 filter in this home. System is now operational.
Performed diagnostic on a 17-year-old Carrier gas system (R-22 type) and found system low on refrigerant charge due to a leak at the heat transfer media coil. Presented customer with options to either refill system and add internal sealers or replace the heat transfer media coil. Customer has decided she would like to speak with our Comfort Consultant regarding possible replacement before making a decision.
Performed diagnostic and found refrigerant leak at the transfer media coil. Discussed options with customer about replacing heat transfer media coil or a full system replacement. Customer will contact us on Tuesday to discuss replacement options with our Comfort Consultant. System is currently operational.
Performed diagnostic and found refrigerant leak at heat transfer media coil on a 2008 Carrier heat pump system in closet. Also, the platform is deteriorating due to water damage and condensation leaking onto first story drywall. Discussed heat transfer media coil replacement options with customer or full replacement. Customer well hold off on any repairs at this time and will contact third-party company for further information. System is operational but out of range.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system with no issues found. Drain lines cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System set to 73° per customer.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. I did find and clear a clog in condensate drain line. Condenser coil cleaned. Electrical disconnect confirmed in and on system set to 73° per customer. Reme Halo unit was not functioning and is under a parts warranty (no labor warranty). Will send estimate for replacement separately.
Performed diagnostic and found heavy amount of oil present at heat transfer media coil. Leak found at heat transfer media coil. Heat transfer media coil and condenser are original equipment from 2004. Gas furnace has been replaced with manufactured date of 2020. Also, large drain pan is rusted out and condensation starting to damage the decking. Both zone dampers are operational. Discussed repair and replacement options with the customer but they will not be making a decision until they speak with their home warranty company.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the systems with no issues found. Electrical disconnects confirmed in and on. Condenser coil cleaned. Systems returned to temperature by customer.
AC Maintenance Kyle, TX
Regular maintenance is often overlooked and left unscheduled- people take their systems for granted. However, what today is a minor issue that could be resolved with a little TLC can quickly turn into a costly HVAC nightmare. With our maintenance plan, we take the guesswork out of the equation and keep your system operating smoothly. Not only does regular maintenance keep your cold and hot air blowing- a well-maintained system will save you money on your monthly utility bill. When your heating and air conditioning unit is struggling, it has to use more power, which will shorten the life of your system as well as cost you more money every minute, long before the system fails.
Money is a great reason to keep up on maintenance, but it’s more than that. Being that dirt is the number one enemy to your HVAC system, the quality of the air in your home or office is greatly affected by your system’s maintenance schedule. It’s important to reduce the amount of pollutants and allergens from the air circulating through your rooms. A well running system is a great way to keep your air clean, and the people in your space breathing freely.