Air Conditioning Repair Services in Martindale, TX
There are a number of reasons why an AC unit may have frozen up:
- Dirty air filter is clogging the air flow to the unit.
- A refrigerant leak.
- Debris covering the evaporator coils in the unit blocking the air flow.
The average cost to repair a home air conditioner in the Martindale TX area ranges from $165 – $550. Most repairs end up being pretty minor and cost around $350. Major repairs, like compressor replacement, could cost as much as $2,000.
Typically, a well maintained central air conditioner should last between 10 – 15 years. Are you considering replacing your old unit? Garner Heating & Air Conditioning offers many quality products along with expert installation services. Contact us today to learn more!
for Martindale, TX
Our Reviews by City
Colburn - Martindale, TX
Great service. Max B. is always helpful and polite .
Crabtree - Martindale, TX
I was very happy with my experience with Garner heating. They came out promptly and worked on two greenhouse heaters that haven’t been working in about 15 years. Excellent service!
Fantastic service from a highly competent technician
Brian - Martindale, TX
Eva - Martindale, TX
Great Service, very friendly , done in a timely maner
Sandra - Martindale, TX
I feel like Ryan really knew his job, Explained every thing he was doing so I could understand it. I have used Garners Heat & Air Conditioning Inc. for many years and never had a reason to change company's .
Complete AC tune-up on 3 systems.
Perform the AC tune-up and everything is working at this time.
Replaced the blower motor at the silver level. Everything is coming on and working at this time.
When I arrived, the customer informed me that when he got home last night around 7pm the system was not cooling. He said that he believes the outdoor condenser fan was on and running but the compressor and the indoor system were not coming on. After turning the system on everything came on and ran like normal. The pressures looked good and I had 9.7 degrees of subcooling and 19.6 degrees of superheat. I checked the drain line and there was no standing water at this time. I cleared the drain anyhow. I did inform the customer that there could be an issue however it is not acting up for me at this time. I checked the delta-t and had 76.8 degrees coming in and it was 55.5 coming out of the supply. Everything is working at this time. The thermostat is set to 76 and it is 76 inside. It started at 81.
When I arrived, I found the air movement system to be non-operational. After performing an inspection of the system, I found that both the blower motor and the fan control board were not working. I informed the customer of the issue and asked if they had been affected by a power surge or lightning strike since we very seldom see both parts go out at the same time. I gave the customer his options and he chose to go ahead and have it repaired at this time. After replacing the parts and performing a routine maintenance inspection everything is working to factory specs again.
When I arrived, I found the air movement system to be in complete failure. I gave the customer his options and he chose to have it replaced. I am ordering the parts and we will be installing them tomorrow between 11-1.
Performed the AC tune-up and everything is working at this time. While performing the inspection I did find ants inside the voltage distributor and gave the customer her options. She chose to go ahead and have it replaced at the platinum option at this time. I was able to replace the voltage distributor, voltage enhancer and install a new compressor saver.
Performed heating tune up on American Standard heat pump system.
Replaced the elbow for the flue pipe on the hanging gas unit in a green house.
Replaced a badd voltage absorber inside the condenser there was not allowing the compressor to come on.
Performing three AC tune ups and changing out a faulty part in Martindale.
Repaired a clients AC system and cleared their condensate drain on River Road.
Performing a platinum safety inspection service. We give you options on repairs. When you choose our top option we return in a year to make sure that your system is working the way it was when made the repair.
Performing a heater inspection and system tune up to ensure everything's operating to the best of its abilities.
Performed heater tune up and system cleaning.
Performing a heater tune up on 1 system to prolong life of unit.
Air conditioner blowing hot air. AC repair on compressor and change air filter. Suggest regular maintenance to help with efficiency and at a minimum replace filter 1-2 times a year.