Heating & Air Conditioning Repair Services in Buda, TX
A well running and properly maintained HVAC system is incredibly important in order to have a happy and comfortable home here in Central Texas. Garner Heating & Air Conditioning have been providing exceptional AC and heating services for nearly 30 years. From simple repairs and maintenance through to a full HVAC replacement and installation in Buda and the surrounding area, our trusted technicians will ensure your system is running optimally and performing well in your home or office.
Garner Heating & Air Conditioning is a proud local company serving residential and commercial clients in Buda and the surrounding Texas Hill Country. We strive to exceed our customers’ expectations, while providing impeccable service. Our years of experience handling air conditioning and heating repair, replacement, and maintenance give us an advantage over our competitors- we specialize in creating a unique comfort system for your home or office. Contact us today!
AC Replacement Buda, TX
When it does come time for an AC and heater replacement, our heating and air conditioning experts in Buda will guide you through every step of the process- from making sure your ducts are clean and properly sealed, vents are directing air to where you need it, and to ensure your space has excellent air flow. They will redesign the system to maximize efficiency and output. Our team will offer advice on insulation and other ways you can support your new air conditioning system, which greatly reduces utility costs.
AC Maintenance Buda, TX
An improperly maintained system will not only make a HVAC replacement necessary sooner- but it also costs you in the meantime in energy costs. A system in good order doesn’t need to run as often or for as long to ensure proper climate control – a poorly running system works overtime for very little benefit. Utility bills can be expensive – this is a great way to save money while enjoying a comfortable home.
Even well maintained systems need repairs occasionally- all of our technicians are N.A.T.E certified and repairs are guaranteed for a year. With decades of experience and stellar customer service, our staff can handle almost any issue with your gas furnace, heat pump, and air conditioning system.
An HVAC system is one of the biggest investments you’ll ever make for the structure you live or work in- a great system is not cheap! The key is to protect this investment by having your system regularly evaluated and maintained to make sure that everything is running smoothly. Many common problems that would shorten the life of your AC and heating units can often be avoided through consistent maintenance. Air conditioner and heating replacements should always be the last resort. You’ll save money by hiring professionals from Garner to keep your system running the way it was meant to.
A few reasons you should replace your air conditioning and heating system rather than repair it in Buda, TX are:
- Your HVAC system is over 10 years old and breaks down often.
- Your energy bills have increased.
- The cost to repair your HVAC system outweighs the cost to replace it.
When your HVAC system becomes ineffective, it will cost you more on energy each month and require multiple repairs. However, if your HVAC system is fairly new, regularly maintained and hasn’t required many repairs in the past, you should have it repaired rather than replaced. Call us today to get your HVAC system repaired or replaced.
An HVAC service should cost around $150-350 in Buda, TX. Having your HVAC serviced is a great way to spot issues before they become more severe. Additionally, regular servicing keeps your HVAC system running more efficiently and extends its service life. The benefits that HVAC maintenance provides greatly outweigh the cost since you save more on energy bills and repair costs. Contact us today to get your HVAC system serviced.
An HVAC tune-up in Buda, TX typically includes:
- A cleaning of your furnace and AC unit.
- An inspection and lubrication of your furnace and AC unit’s parts.
- Minor repairs.
To get the most out of tuning up your HVAC system, you should have your HVAC system tuned up once before summer and once before winter. Getting your HVAC system tuned up before peak seasons allows your HVAC to run more efficiently and require less repairs. To get your HVAC system tuned up, give us a call today.
The average air conditioning repair cost in Buda, TX is about $350-$600. The cost for the air conditioning repair can vary due to:
- The kind of air conditioning repair required.
- The level of the air conditioning repair required.
- The HVAC contractor’s hourly fee.
The overall price of the air conditioning repair can also fluctuate depending on if the repair requires replacement parts. To find out more about getting your air conditioning system repaired, contact us today.
It costs around $3,000-$7,000 to replace a central air conditioning unit in Buda, TX. The cost can vary depending on:
- The size of your home.
- The type of central air conditioning unit you want installed.
- The cost to remove your old AC unit and install the new one.
Another thing that can impact the price of your central air conditioning unit replacement is if your air ducts also need to be replaced. To get your central air conditioning system replaced, call us today.
Your central air conditioner should be checked at least once a year, right before the cooling season in Buda, TX. Getting your central air conditioner cleaned and inspected before your area’s peak cooling season will ensure that your central air conditioner is able to run smoothly and efficiently. Additionally, regular servicing can help to extend the service life of your central air conditioner. To get your central air conditioner serviced, give us a call today.
See what your Buda neighbors are saying about our services below.
for Buda, TX
Our Reviews by City
Great service and excellent employees
Cummings Darlis - Buda, TX
Great service and customer service
Hammond - Buda, TX
Nothing but the best and very informative
Great attitude great service
Condel - Buda, TX
Great install on our new A/C system
Haffner - Buda, TX
Quality work and excellent customer service.
Rogers - Buda, TX
Bogue - Buda, TX
Rogers - Buda, TX
Technician arrived on time and was very thorough and professional .
Clay - Buda, TX
Garner has a great reputation for doing quality work at a fair price so I call them whenever I have heating or AC problems. During the recent ice storm I lost heat in my home and called Garner. In a short time I received a courtesy call from George letting me know he was on his way. He was a very knowledgeable and experienced tech and was able to quickly diagnose and repair the problem explaining what he was doing every step of the way. I have now used Garner twice and each time they have sent out a tech who is both knowledgeable as well as highly customer service oriented. Would highly recommend Garner Heating and AC.
Excellent Service! Honest trustworthy!!
Gooding - Buda, TX
Jistel - Buda, TX
Performed diagnostic and found system not cooling due to insufficient amount of refrigerant charge. Completed leak test and found a leak at the evaporator coil. Presented options for repairs and customer chose to add refrigerant and sealant additive. I did disclose to the customer that sealer is a temporary fix and the refrigerant could leak out in a day, month or years. System is operational.
Installed Carrier Performance Series system in attic. Added new drain pan, plenums, and vibration isolators. Installed new line filter dryer and pressure tested system for extensive leak check. Pulled deep vacuum and charged system to factory specs. Sealed all pressure points with mastic tape and air lock. Added new upstairs disconnect with full system surge protection. Installed new Edge thermidistat and benchmarked system. Preformed maintenance on upstairs system with new SS-2 and SS-3 safety switches. Cleared both drains with C02 and replaced outside voltage enhancement system. Checked charge and cleaned coil.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. Outdoor voltage enhancement system on condenser found to be low in value. Options presented to customer, and they have decided to move forward with repairs. Replaced voltage enhancement system, cleared/treated drain line, and cleaned condenser coil. Electrical disconnect confirmed in and on. System set to 75° per request of the customer. Please see attached checklist for full tune-up details.
Performed Deluxe tune-up. System was found to have very low refrigerant charge. Options presented but customer has declined charging with refrigerant or inspecting for leak. Due to the age of the system the customer would like to have our Comfort Consultant come out to provide a quote for system replacement. Please see attached checklist for full tune-up details.
Performed AC cool check. Checked electrical, mechanical, safety and performance of the system. Found and tightened loose wires on control board. Drain lines cleared and treated. No other issues found. Electrical disconnect confirmed on. System set to auto schedule per customer request. Please see attached checklist for full tune-up details.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system with no issues found. Drain lines cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System set to 76° per request of the customer. Please see attached checklist for full tune-up details.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. Drain lines cleared and treated. System was found to have low refrigerant charge. Performed a leak check but no leak in the system was able to be located. Charged with 6 ounces of R-410A. System now operating within specs. Electrical disconnect confirmed in and on. System set to 80° per request of the customer. Please see attached checklist for full tune-up details.
Performed cooling tune-up on an American Standard gas system. Please see attached checklist for full tune-up details.
New heat transfer media coil and filter dryer has been installed. Refrigerant charge back on target. Performance testing completed and system is operational.
When I arrived, the customer informed me they heard a strange noise coming from the air handler. I performed a diagnostic and could not get it to replicate the noise and the system was cooling for me at this time. However, the system is old and in poor condition. I suggested a few things we could do to the system but can not promise the noise will not return since I could not replicate. Customer chose to wait on any repairs and will call us if the noise presents itself again.
Performed bronze level repair on the blower motor. After performing the repair everything is coming on and working the way it is supposed to at this time.
Performed the AC tune-up and everything is working at this time. While performing the inspection I did find the voltage enhancement system to be low on value. I also found that the condenser fan motor was pulling 1.2a when it is rated at 1.0a. I presented my findings to the customer, but they declined all repairs at this time. Please see attached checklist for full tune-up details.
Performed the diagnostic and found the voltage enhancement system under tolerance preventing cooling cycle. Present options and customer decided to move forward with replacement of the voltage enhancement system. Completed repair and performance testing. System is now operational.
Performed AC cool check and found a leak in the evaporator coil. Will return to replace coil once coil received from manufacturer. Please see attached checklist for full tune-up details.
Installed Carrier Comfort Series gas system in upstairs closet. Rebuilt drain line with SS-2 safety switch. Also rebuilt gas line and installed line filter dryer. Pressure tested system for extensive leak check and pulled deep vacuum. Installed zone board and Ecobee Pro thermostats. Added ductwork zoning and benchmarked system.
Performed AC cool check. Checked mechanical safety, electrical and performance of system and found no issues. Drain lines were cleared and outside condenser coil was cleaned. Customer also renewed their maintenance plan. See attached checklist for full tune-up details.
Performed cool check on a Carrier Infinity system. Checked mechanical, electrical, safety and performance of the system and no faults found. Drain lines cleared and outside condenser cleaned. Please see attached checklist for full tune-up details.
After performing the diagnostic, I found that the primary drain line was severely clogged and had backed up in the system as well as the plenums. I also found the voltage enhancement system in the condenser to be weak and undervalued. I presented the customer with his opinions and he chose to have the clogged drain repaired at the bronze level but declined repairs to the voltage enhancement system. After performing the bronze level drain repair everything is coming on and working at this time. I also suggested that the customer leave the fan in the on position for a week to help dry out the insulation.