Expert HVAC Care Serving the Residents of Buda, TX
If you want your Central Texas home to stay cozy and comfortable, you have to make sure your HVAC system is running well. Like any major appliance in your home, though, it's important to take care of it, and that means providing proper maintenance and repairs when needed. Garner Heating & Air Conditioning is your partner in maintaining your HVAC system so it remains in top shape, or helping you choose the most efficient and capable solution when it needs to be replaced.
The HVAC Service You Want, The Quality You Need
Garner Heating & Air Conditioning offers the full spectrum of services to take care of every aspect of your home's HVAC system.
A few reasons you should replace your air conditioning and heating system rather than repair it in Buda, TX are:
- Your HVAC system is over 10 years old and breaks down often.
- Your energy bills have increased.
- The cost to repair your HVAC system outweighs the cost to replace it.
When your HVAC system becomes ineffective, it will cost you more on energy each month and require multiple repairs. However, if your HVAC system is fairly new, regularly maintained and hasn't required many repairs in the past, you should have it repaired rather than replaced. Call us today to get your HVAC system repaired or replaced.
An HVAC service should cost around $150-350 in Buda, TX. Having your HVAC serviced is a great way to spot issues before they become more severe. Additionally, regular servicing keeps your HVAC system running more efficiently and extends its service life. The benefits that HVAC maintenance provides greatly outweigh the cost since you save more on energy bills and repair costs. Contact us today to get your HVAC system serviced.
An HVAC tune-up in Buda, TX typically includes:
- A cleaning of your furnace and AC unit.
- An inspection and lubrication of your furnace and AC unit’s parts.
- Minor repairs.
To get the most out of tuning up your HVAC system, you should have your HVAC system tuned up once before summer and once before winter. Getting your HVAC system tuned up before peak seasons allows your HVAC to run more efficiently and require less repairs. To get your HVAC system tuned up, give us a call today.
The average air conditioning repair cost in Buda, TX is about $350-$600. The cost for the air conditioning repair can vary due to:
- The kind of air conditioning repair required.
- The level of the air conditioning repair required.
- The HVAC contractor’s hourly fee.
The overall price of the air conditioning repair can also fluctuate depending on if the repair requires replacement parts. To find out more about getting your air conditioning system repaired, contact us today.
It costs around $3,000-$7,000 to replace a central air conditioning unit in Buda, TX. The cost can vary depending on:
- The size of your home.
- The type of central air conditioning unit you want installed.
- The cost to remove your old AC unit and install the new one.
Another thing that can impact the price of your central air conditioning unit replacement is if your air ducts also need to be replaced. To get your central air conditioning system replaced, call us today.
Your central air conditioner should be checked at least once a year, right before the cooling season in Buda, TX. Getting your central air conditioner cleaned and inspected before your area's peak cooling season will ensure that your central air conditioner is able to run smoothly and efficiently. Additionally, regular servicing can help to extend the service life of your central air conditioner. To get your central air conditioner serviced, give us a call today.
HVAC Service You Can Trust
Your HVAC system is one of your biggest investments,. You don't want to leave it's care to just anyone. Garner Heating & Air Conditioning has decades of experience powering our professional technicians, and a family-first focus that means we aren't satisfied until you are. It doesn't matter if you're looking for someone to handle regular maintenance, interested in upgrading your system or want to explore options to improve your indoor air quality, Garner has you covered.
But if you don't want to take our word for it, ask your neighbors! Read below to hear about what others in Buda, TX have been saying about our service:
for Buda, TX
Our Reviews by City
Richard - Buda, TX
Sherolyn - Buda, TX
Garner has done several AC jobs for me. Always easy to deal with and exceptional service. Highly recommend them
Martha - Buda, TX
We’ve had maintenance contracts with Garner since 2006! We continued to use them because of their great service. Their employees are extremely knowledgeable and will work diligently to meet your needs!
New Compressor Needed
Lance - Buda, TX
All possible fixes were eliminated until a new compressor was the only solution. Jason was very professional and thorough in explaining and fixing our system problem. Good service at a fair price. Much appreciated.
The Best Service ever!
CC - Buda, TX
The team of 2 showed up to their appt on time They also sent us messages when they were on their way. They were friendly, kind, knowledgeable. They checked out the inside the continued outside found the problems and gave me an estimate of how long it would take and what I was looking at in price. They helped keep the carpet free of derbies by wearing shoe covers (even though I told them they didn’t have to) They got the air conditioning working and it’s blowing snowballs. I am glad they sent this two man team to my home they were totally awesome! Great price for the service provided. I would totally recommend this company to anyone for all their heating and air conditioning needs they ROCK!
Ed - Buda, TX
On time, efficient,thorough,and explained things completely
Donald - Buda, TX
Quality Company, Quality Employees
Red - Buda, TX
We've been dealing with Garner for almost 20 years and never have we had a bad experience. In my opinion they are fantastic.
Great Service, explained everything that they were going to do
William - Buda, TX
Greg - Buda, TX
Matt with Garner Heating and Air did a great job on our maintenance for our HVAC system. Highly Recommend!
Performed maintenance on the AC system. During system maintenance, I cleared the drain line and cleaned the condensing coil. Also checked pressures and system is in good condition. Checked capacitor with no issues. System is operational at this time.
Performed service diagnostic. Diagnostic found that the capacitor on the condenser unit had failed. Options for repair were presented to customer and they chose to have the capacitor replaced. Repair was completed. Electrical disconnect confirmed in and on. System was running at the time of departure.
Blower wheel was removed, cleaned, and then reinstalled. Electrical disconnect confirmed in and on. System was running at the time of departure.
Performed service diagnostic. Diagnostic found that the condenser fan motor was not running due to a failed fan capacitor. Compressor was in thermal lockout. Options for repair were presented to customer and they chose to have the capacitor replaced and join our maintenance plan. Compressor was cooled and fan capacitor was replaced. Electrical disconnect confirmed in and on. System was running at the time of departure.
On arrival, found the outdoor exhaust removal system had failed causing the refrigerant circulation system to stop running. Presented repair options. Replaced the outdoor voltage enhancement system, along with a new exhaust removal system. Also cleaned the outdoor heat transfer media coil.
Checked system and discovered that the temperature split was a high. We raised the fan speed and checked the charge. Then we charged the system to factory specifications and checked the capacitor which was still within range. System is operational upon departure.
Performed the AC tune-up. While performing the inspection I did find deficiencies with the system and the client chose to have the mandatory repairs done at this time. After performing the repairs, the system is operational.
Performed the AC tune-up. While performing the inspection I did find deficiencies with the system. I presented the client with his options, and he chose to have the mandatory repairs done at this time. After performing the repairs everything is coming on and working at this time.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. No major issues were found. Drain line cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System was running at the time of departure.
Performed cool check on the AC system. Checked blower, coil, and all electrical with no major issues found on the furnace or coil. Cleared drains. Check capacitor starter and breaker. When checking charge, I did find that the system was low on refrigerant. Gave the client options and he chose to charge system to proper specs. Completed repair, cleaned condensing coil, and set thermostat to customer preference. System operational.
Performed scheduled maintenance on two AC systems. Cleared drains and checked wiring on both systems. Cleaned and washed both condensers. Checked caps and pressure. On the 5-ton system, the capacitor was bad, and I gave the client options, and she chose to have it replaced. No other major issues were found. Repair completed and systems cycled. Thermostat put back to customer preference and disconnects checked and in the on position.
Installed new Rheem heat pump system in attic. Replaced supply plenum and hard ducted to return with AprilAire media filter cabinet. Also replaced flex duct, buckets, and registers. Rebuilt drain line with SS-2 and SS-3 safety switches. Installed new line filter dryer and pressure tested system for extensive leak check. Pulled deep vacuum and weighed in factory charge. System working at this time.
Diagnosed bad capacitor. Gave client options and he chose to have it replaced. Replaced capacitor on site and secured it in place. Tested system and it is operational.
Performed service diagnostic. Diagnostic found that the capacitor on the condenser unit had failed and the disconnect for the condenser unit was broken. Connections are intact on the disconnect but the pull handle was missing. Options for repair were presented to customer chose to have both components replaced. Capacitor was replaced and the system is up and running. Repair was completed. Disconnect confirmed in and on. System was running at the time of departure.
Customer stated that water was leaking out of system. Found that the drain pan had debris in the primary that had backed up causing the pan to overflow. Presented repair options and customer chose to have the pan and drain cleared. Customer also chose option to clean coil and blower motor. Repairs were completed and system is operational.
Installed new Rheem 4-ton gas system. Re-piped and insulated condensate drain line and installed float switches. Installed new inline filter dryer on cooper line set. Pressure tested with dry nitrogen and pulled a vacuum on the line set. Weighed in refrigerant and charged system to factory specs. Replaced both supply and return plenum as well as replace all zoning components (16x16 dampers and zone board). Reattached ductwork to each zone and sealed all joints and connections with an airlock mastic. System operational.
System was not cooling, and I diagnosed that the capacitor had failed (40/7.5 cap and was reading 10/2.8). Gave the customer options and he chose to have the capacitor replaced. Tested system: pressures were good and so was the temp split. System is operational upon departure.
Installed new Rheem system in attic. Installed new temporary supply and return plenums to preexisting ductwork. Installed media filter and new Ecobee thermostat. Added filter dryer and pressure tested system for extensive leak check. Pulled deep vacuum and weighed in factory charge. Rebuilt drain line with SS-2 and SS-3 safety switches. System operating at this time.
Performed maintenance on the AC system. Also checked air flow and cooling in the guest room. Found no issues other than the windows were open allowing heat into the room. I did find the cap under value and presented Ralph with repair options. He chose to have the capacitor replaced today. Completed repairs and system operational.
Performed maintenance on the AC system. I did find the capacitor to be failing and the fan motor showing signs of overheating. I presented Dena with options to repair, and she chose to change the capacitor and wait on fan motor. Completed repair and performed safety testing. System operational.