Expert HVAC Care Serving the Residents of Buda, TX
If you want your Central Texas home to stay cozy and comfortable, you have to make sure your HVAC system is running well. Like any major appliance in your home, though, it's important to take care of it, and that means providing proper maintenance and repairs when needed. Garner Heating & Air Conditioning is your partner in maintaining your HVAC system so it remains in top shape, or helping you choose the most efficient and capable solution when it needs to be replaced.
The HVAC Service You Want, The Quality You Need
Garner Heating & Air Conditioning offers the full spectrum of services to take care of every aspect of your home's HVAC system.
A few reasons you should replace your air conditioning and heating system rather than repair it in Buda, TX are:
- Your HVAC system is over 10 years old and breaks down often.
- Your energy bills have increased.
- The cost to repair your HVAC system outweighs the cost to replace it.
When your HVAC system becomes ineffective, it will cost you more on energy each month and require multiple repairs. However, if your HVAC system is fairly new, regularly maintained and hasn't required many repairs in the past, you should have it repaired rather than replaced. Call us today to get your HVAC system repaired or replaced.
An HVAC service should cost around $150-350 in Buda, TX. Having your HVAC serviced is a great way to spot issues before they become more severe. Additionally, regular servicing keeps your HVAC system running more efficiently and extends its service life. The benefits that HVAC maintenance provides greatly outweigh the cost since you save more on energy bills and repair costs. Contact us today to get your HVAC system serviced.
An HVAC tune-up in Buda, TX typically includes:
- A cleaning of your furnace and AC unit.
- An inspection and lubrication of your furnace and AC unit’s parts.
- Minor repairs.
To get the most out of tuning up your HVAC system, you should have your HVAC system tuned up once before summer and once before winter. Getting your HVAC system tuned up before peak seasons allows your HVAC to run more efficiently and require less repairs. To get your HVAC system tuned up, give us a call today.
The average air conditioning repair cost in Buda, TX is about $300-$3500. The cost for the air conditioning repair can vary due to:
- The kind of air conditioning repair required.
- The level of the air conditioning repair required.
- The HVAC contractor’s hourly fee.
The overall price of the air conditioning repair can also fluctuate depending on if the repair requires replacement parts. To find out more about getting your air conditioning system repaired, contact us today.
It costs around $7,000-$15,000 to replace a central air conditioning unit in Buda, TX. The cost can vary depending on:
- The size of your home.
- The type of central air conditioning unit you want installed.
- The cost to remove your old AC unit and install the new one.
Another thing that can impact the price of your central air conditioning unit replacement is if your air ducts also need to be replaced. To get your central air conditioning system replaced, call us today.
Your central air conditioner should be checked at least once a year, right before the cooling season in Buda, TX. Getting your central air conditioner cleaned and inspected before your area's peak cooling season will ensure that your central air conditioner is able to run smoothly and efficiently. Additionally, regular servicing can help to extend the service life of your central air conditioner. To get your central air conditioner serviced, give us a call today.
HVAC Service You Can Trust
Your HVAC system is one of your biggest investments,. You don't want to leave it's care to just anyone. Garner Heating & Air Conditioning has decades of experience powering our professional technicians, and a family-first focus that means we aren't satisfied until you are. It doesn't matter if you're looking for someone to handle regular maintenance, interested in upgrading your system or want to explore options to improve your indoor air quality, Garner has you covered.
But if you don't want to take our word for it, ask your neighbors! Read below to hear about what others in Buda, TX have been saying about our service:
for Buda, TX
Our Reviews by City
Pam - Buda, TX 78610
Omar was very thorough and a pleasure to work with! Keep up the good job Omar!
Excellent quality of work
Greg Johnson - Buda, TX 78610
Very professional and exacting inthe great quality of work. Replaced all the ductwork and ductwork components in six hours with crew of four. Nathan's communication skills are outstanding. He explained in detail what was done and why along with next steps if there are any issues or adjustments necessary. Max, the project manager was fabulous and really sold me on Garner along with positive recommendations from neighbors who had previous good experience with the company. I highly recommend Garner to anyone requiring ductwork replacement. We'll be using them for other HVAC work when needed. Many thanks!!
Derrick - Buda, TX 78610
Brian - Buda, TX 78610
On time. Thorough inspection. Very likable.
Andree - Buda, TX 78610
My husband and I were very happy with the duct work done. Every one was very efficient and they cleaned up . No mess for me to clean.
Dryer vent cleaning
Richard - Buda, TX 78610
Excellent service. Both gentlemen were kind, courteous & professional.
Helene - Buda, TX 78610
Response from Garner Heating & Air Conditioning Inc:
We are so grateful for your 5-star review. Thanks for sharing your rating with us and the community.
Kathryn - Buda, TX 78610
Prompt, professional and efficient.
Bruce - Buda, TX 78610
Saralyn Heath - Buda, TX 78610
We always get great service from Garner but Elija Dover and his team mate were exceptional. They were polite friendly and very knowledgeable.
Performed the AC tune-up. No major issues found. System was running at completion of job.
Performed service diagnostic. Diagnostic found that the that the system was operational. The customer’s son had told her that the condenser unit was making a noise it had not before. Capacitor on the condenser unit is below value. Options for repair were presented to the customer and they chose to have the capacitor replaced today. Repair was completed. System was function checked and was running at the time of departure.
Performed cooling maintenance. Checked electrical, mechanical and performance of the system. Cleared and treated drain line and washed the condenser coil. No major issues were found. System is on and running at this time.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. No major issues were found. Drain line cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System was running at the time of departure.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. No major issues were found. Drain line was cleared and treated. Condenser coil cleaned. Electrical disconnect confirmed in and on. System was running at the time of departure.
Honeywell thermostat was installed for the upstairs zone. System was function checked and both zones on the system are operational. I showed the customer how to operate the thermostat, where his 20x25x4 Honeywell filter is located as well as where and when to treat the primary condensate drain. System was running at the time of departure.
Performed the AC tune-up. Customer has decided to have us install our Stage 2 Breathe Easy package. We installed the high voltage to the power pack and wired it into the furnace’s main power supply. We located a good spot for the ionizer and installed it in the supply side of the system. This way the ionized air moves through the home charging the dust particles throughout the home and turning them from snowflakes to snow balls. The larger particles will then get caught by the filter. System is working at completion of service.
HVAC Repairs near Joy Hollow. Responding to a client's request for HVAC repairs, we arrived on-site and diagnosed low refrigerant levels as the issue. Replenishing the refrigerant to the manufacturer's recommended levels, we successfully restored the system to full operation. Before leaving, we also took the initiative to replace the filters, further optimizing the performance of the HVAC system.
HVAC Maintenance Service near Bristol Rd. As part of the spring maintenance check-up, we visited the client's residence in TX to assess their HVAC system. Conducting a thorough inspection of all components, we ensured that the system was functioning optimally and would continue to provide efficient service. Additionally, we identified a clogged condensate line and promptly cleared it, resulting in improved performance and functionality of the entire system.
Air Conditioning System Replacement Service near Rosemary Hollow. During a routine maintenance check-up, we discovered that the client's air conditioning unit was in need of replacement. Today, we arrived to install the new system, meticulously removing the old unit from the home. Carefully installing the new system, we thoroughly checked all components to ensure proper operation. The new A/C system is now functioning in accordance with the manufacturer's specifications, providing reliable cooling for the client.
Air Conditioning Repair near Garlic Creek Dr. When a client reported an issue with their A/C system, we promptly responded and investigated the problem. Upon inspection, we identified a faulty contactor as the culprit. After efficiently replacing the contactor, we thoroughly tested the unit to guarantee optimal performance and quality. As a result, the air conditioning system is now restored and operating smoothly once again.
Ductwork Replacement near Sequoyah St. We responded to a client's request and assessed the condition of their ductwork. After determining the need for replacement, we arrived today to carry out the task. After methodically removing and discarding the old ductwork throughout the home, we diligently installed and sealed the new ducting, ensuring a more reliable system for the residence.
Performed semiannual maintenance on one heat pump cooling system. Inspected all Performance, Mechanical and Safety Systems. Verified everything was working within manufacture’s specifications for operation. I did find the system low on refrigerant. Homeowner has decided to have the system recharged. Repair completed and everything is working at this time.
Performed semiannual maintenance. Inspected all Performance, Mechanical and Safety Systems. Verified everything was working within manufacture’s specifications for operation. Everything is working at this time.
Performed AC cool check. Checked electrical, mechanical, safety, and performance of the system. No major issues were found. Drain line cleared and treated. Condenser coil cleaned.
Performed semiannual maintenance on one heat pump cooling system. Inspected all Performance, Mechanical and Safety Systems. Did note the Honeywell 20x25x4 Filter has not been changed in two years and is extremely clogged up causing an airflow restriction on the cooling system which has drastically reduced cooling capacity of the system. Homeowner said she will order new set of filters and change them once they arrive. Everything is working at this time.
Performed the AC tune-up. I did find that the UV lights were not on. No other major issues were found. UV lights were repaired and are now operational. Covered under Garner's warranty.
Performed the AC tune-up and no major issues were found
Performed service diagnostic. Diagnostic found that the contactor on the condenser unit, the circuit breaker for the condenser and the surge protector for the condenser have all failed. Options for repair were presented to the customer and they chose to have all three repairs completed. Contactor, breaker and surge protector were replaced. System was function checked and is running upon completion of repairs.
Performed the AC tune-up. I did inform the homeowner that his capacitor is just below the allotted 5%.