Air Conditioning Repair Services in Dripping Springs, TX
Some of the symptoms of bad indoor air quality in your Dripping Springs home are:
- Dry throat, nose and eyes.
- Dry or irritated skin.
- Increased allergies indoors.
It costs around $350-$600 to repair a home air conditioner in Dripping Springs. Some things that can cause the price of the repair to vary include:
- How extensive the repair is.
- What type of repair is required.
- Whether replacement parts are needed.
Some repairs can be fairly inexpensive, whereas refrigerant leaks can be expensive due to the cost to replace the refrigerant in your AC system. To get your home air conditioner repaired, call us today.
Yes, AC tune ups are worth it in Dripping Springs. Some of the benefits of having your AC unit tuned up are:
- Your AC unit runs more smoothly.
- Your AC unit uses less energy.
- Your AC unit breaks down less.
Another benefit to having your air conditioner tuned up is that it will require less repairs and cool your home better. To get the best results, you should have your AC unit tuned up at least once a year. To get your AC unit tuned up, give us a call today!
There could be a number of issues with your air conditioner that is causing it to blow hot air in your home near Dripping Springs TX. Try troubleshooting a few common reasons first before calling a technician:
- Turn the thermostat to AUTO if it was set to ON so that the unit can complete a full cooling cycle.
- Change the air filter in order for the air to be able to circulate properly throughout your home.
- Clean the outdoor unit so that the unit can expel warm air from your home.
- Check the circuit breaker in case it has tripped which will cause it to still operate but not produce cool air.
If you have checked these items and your unit is still not cooling the house, your next step should be a call to a professional. The expert technicians at Garner can diagnose any AC repair issue and fix it effectively at an affordable rate. Contact us online today for an appointment.
On average, in the Dripping Springs TX area you can expect to pay anywhere from $250 – $1,500 to a freon leak repair. It can be hard to estimate the cost of a freon leak in an air conditioner as the price depends almost entirely on where the leak is located and the size of it. A hard to find severe leak could take technicians all day to repair, which will increase costs of labor.
For a more accurate estimate on repair services, the knowledgeable team members at Garner are happy to help. Contact us today to learn more about freon leaks and their costs!
An AC compressor works to move refrigerant throughout the unit to ultimately produce the cool air for your home. When it goes bad, there are a few signs you should be on the lookout for:
- Weird noises.
- Unit will not start.
- Air is not cooling.
- Breaker keeps tripping.
- Less air coming from vents.
for Dripping Springs, TX
Our Reviews by City
Merz - Dripping Springs, TX
Always great service
Gonzales - Dripping Springs, TX
All employees are polite and know what they're doing.
Don came out here by 130 on a1to5 window. Great service, knowledgeable and professional. Will recommend your company.
Paul - Dripping Springs, TX
Awesome service as always!
Penne - Dripping Springs, TX
We are so glad we take advantage of the maintenance package offered. The technicians are always professional and courteous. It’s much appreciated sharing the work done and knowing how our units are performing as well as what to expect in the future with our aging units. Thank you!
Replaced Reme Halo under warranty. Spoke to him about if the Halo fails again then we need to discuss other options.
Reme Halo replaced under warranty.
Performed heater tune-up on heat pump system. Pulled and cleaned blower wheel and housing. Cleaned coil in place. Cleaned air handler cabinet. System is operating properly at this time.
Installed new heat kit in guest side of home to replace the one that had failed. Also installed a new bathroom exhaust fan for the last bathroom in the home.
Performed QC. Set gas pressures for both high and low heat. System looks good and no issues found.
Performed diagnostics on a 3 1/2-ton Carrier system. Found the heat kit damaged Reme Halo burnt out. Parts house is closed so we will contact them tomorrow for details on any possible warranty. Will reach out to Speedy Gonzalez around 9am for a good time to return and repair all issues. $125 Was collected and will be in reimbursed if option chosen.
When I arrived, I found the mini split system to be slightly low on refrigerant. The customer showed me pictures of the unit iced up. I checked the flare connections as well as the coils and did not get any hits or bubbles at this time. I gave the customer his options and he chose to have refrigerant added and is going to keep an eye on it. Everything is working after completion of repairs.
Ran new copper line set for ductless system in study. Also ran new high voltage disconnect to unit and control wiring. Pulled deep vacuum and weighed in new R-410A refrigerant. Insulated line set and strapped line. Washed and cleaned outside condenser. System operating at this time.
Routine maintenance on American Standard 5-ton heat pump. Drain treatment performed and filter in good condition. Found voltage enhancement system low. Two new single 15/35 voltage enhancement system have been installed. System up and cooling.
New air removal system has been replaced at air handler and amps are now in range. Refrigerant charge and outdoor voltage enhancement system verified in spec. System back up and cooling.
Conducted cooling check 2020. Found that the voltage enhancement and distribution systems both had faults. Client chose Platinum repair to solve the issues. I made the repairs and checked the system in cool. The system is cooling properly at this time.
Conducted cooling check 2020. The system is cooling properly at this time.
I find the primary drain line to be completely clog and the secondary drain pan to be full of water and the safety float switches cutting off the outdoor unit. I clear the primary drain line and pump all the water out of the secondary pan down the primary drain line. I also treat the drain line. Everything is free flowing at this time. No charge per Ryan. I did inform the customer that if it backs up again that we will need to re-pipe the drain line out of the house in a different location.
Install new supply plenum to upstairs slab coil. Install dampers for air control and seal buckets and takeoffs with air lock. Measure upstairs CFM and adjust for maximum comfort upstairs.
Checked the electrical, thermostat, and cleared the drain line. The system is working properly at this time.
Please see the attached picture and quote for ductwork repairs.
Found that, while the upstairs system is capable of cooling, the capacity of the system is cut way down because of the poor installation of the evaporator coil. This can cause catastrophic failure to the compressor and will be much more expensive to run.
Installed new 4 ton carrier system in sunset canyon
Replaced a bad combination and ignition system inside the American Standard gas furnace.