Since 1988, residents of Mustang Ridge, TX have trusted Garner Heating & Air Conditioning to provide professional work and outstanding service for all of their HVAC needs. If you’re looking for a provider you can count on, call today!
If you’d like to know what your neighbors in Mustang Ridge, TX think, just check out their reviews below!
for Mustang Ridge, TX
Our Reviews by City
Performed service diagnostic. Diagnostic found that the system was operational and was cooling. The bedroom that was not cooling was well was getting cool air however the window faces the sun from the early afternoon through sunset. I completed my diagnostic and found that the system is low on refrigerant. Options for repair were presented to the customer and they chose to have the system charged with refrigerant. 3lbs of R-410A was added to the system and is cooling at 8.7 degrees of sub cooling.
Performed inspection. I found that the outdoor capacitor has failed. I presented the customer with repair options, and they chose to have the capacitor replaced today. Completed repairs and system is now operational.
After performing the diagnostic, I found that the primary drain line was backed up and tripping the safety float switch. I also found that the battery capacitor was bad. I called the landlord and presented him with his options. He chose to have them both replaced at this time. Repairs completed and system is operational.